Desalination Train Internal
& External Major Overhauling
Facility Name: Hub Power Station
Equipment Name: Desalination Unit
Number of Equipment: 01- Train
Service: Sea water, the job of this equipment to produce service water through the process of desalination.
Service Temperature: 70 Degree 'C (158'F)
Service Pressure: Negative Pressure / Vacuumed.
Sulpher particles venting from Exhaust Stack along with dew at night creates sulfuric acid on external roof side, which causes pitting and even through holes, vacuum hence broke and efficiency of the unit fall.
Erosion/ Corrosion protection is required against sea water service along with 70'C (158'F) of continuous temperature. During major outage facility wants to repair all these weak areas with Cold Rebuilding System because Hot Water was not an option due to the presence of Rubber Lining Inside which could be damaged obviously during welding.
After cold repair a perfect protective coating was also required which can sustain mild sulfuric acid phenomena and atmospheric conditions.
> All roof area was grit blasted,
> Protective Coating application of roof was carried out with UPS 401 / 402 with a subsequent coat of UV Resistance Coating.
> Top Coat on all external surface with UV resistance grade coating
> Detached/ damaged rubber lining was removed and surface was grit blasted,
> Protective coating application with UPS 403 UC Epoxy Coating